Trusted family company since 1965
Complete installations for your home
Your local award-winning team
Free no-obligation home surveys
All drinking water systems that filter your water will require their water filter cartridges to be replaced when they become exhausted.
You can either come to our showroom to collect your replacement filter cartridge or we can post it directly to your home. Call us today.
Collect your block, tablet or granular salt from our premises in Holt during opening hours.
Mon – Friday: 9am – 5pm
Saturday: 9am – 12noon
Bank Holiday Weekends: Closed
258 The Common
Holt (Nr Bradford-on-Avon)
WARNING To avoid injury and/or property damage, system must be depressurised before attempting to change cartridges.
See Step 1 for proper procedure.
If you are unsure about any part of the cartridge replacement procedure, contact us for assistance.
If you are outside the South West of England, find the dealer nearest you using Kinetico’s website.
This cartridge (Part No. 9306B) is designed for the reduction of taste, odour, and aesthetic chlorine.
This replacement component is for use exclusively in the Kinetico Drinking Water Filter Model 7000 and as a postfilter in Drinking Water Systems.
In systems with MACguard (Drinking Water Filter Model 7000 & 7500) The MACguard filter automatically shuts off/reduces flow to a fine trickle after 1,850 litres (approx. 500 gallons) of water have been processed.
Cartridge replacement is required to restore water flow.
In Drinking Water Systems without MACguard you should replace your prefilter and postfilter cartridges at least once per year. Installation must comply all applicable laws and regulations.
Turn off the feed water to the unit. If you have a Kinetico Drinking Water System with a storage tank, shut off the valve on the storage tank by rotating the handle (if included). Open the drinking water tap to depressurise the system All air/water flow must cease before continuing with Step 2. This may take several minutes.
Disengage the cartridge by turning clockwise. Pull the cartridge down from the head. Discard the cartridge.
Fill the cartridge with tap water to expel any air.
Insert the cartridge into the head and rotate anti-clockwise.
Turn on the feed water. If you have a Kinetico Drinking Water System with a storage tank, open the valve on the storage tank (if included).
Allow the tap to remain open for approximately 15 minutes. It is necessary to rinse a minimum of two tank fills to purge air and rinse carbon fines.
Close the tap.
Check for leaks.
Replacement is complete.